- Verify the device is powered by 120VAC.
The LED should be illuminated when the device is in the OFF position. If this is not the case, check wiring.
If wiring is correct and the device still does not power, replace the device.
- Verify the device controls the connected circuit using its own local control (tapping the middle button ON/OFF).
If the circuit does not respond, check the lamping to ensure the bulb is not in need of replacement.
Verify the sound of the internal relay opening and closing can be heard when turning the device ON and OFF.
Verify the load wire is connected properly to the circuit. Recall that the two blue wires represent input and output voltage for the switched circuit. If the circuit is a 120VAC lighting circuit, then one side of the blue should be tied with the black line wire, while the second blue should be wired to the load.
If the device still does not control the circuit, replace the device
- If the device operates the circuit properly but is not being controlled properly by another Evolve device, do NOT replace the hardware.
First, verify the device is installed within the correct guest room. Check the sticker on the device.
Try “Resending All Data” to the device using the Evolve Device Replacement Tool
Reset & “Replace Fail” the device into the proper network